Fangkuai’s gas hot water boiler adopts advanced fully premixed plane combustion technology to increase the heat load of the furnace volume and reduce the formation of high-temperature NOX. The convection heating surface adopts a combination of natural convection and forced convection in a large space to ensure uniform washing of the heating surface and reduce the requirements for boiler water quality. This boiler is a condensing boiler with an overall layout based on rigorous thermal theoretical calculations and years of experience in thermal layout pipe networks and uses CFD (numerical simulation) technology. It is very suitable for low-temperature heating systems and solves the low-load and chronic disease of low-temperature corrosion.
The gas-fired hot water boiler with fully premixed plane combustion technology and wing technology can optimize and improve the structure and layout of the boiler and burner, making the volume of the boiler greatly reduced, which is 60% smaller than that of ordinary condensing hot water boilers.
Gas-fired boilers are used as backups for each other, which greatly improves equipment utilization, investment utilization, and operational safety. The system load adjustment ratio is improved, the outlet water temperature is more constant, the system operation efficiency is further improved, and the service life of the boiler is automatically balanced.
It can realize several major functions such as real-time monitoring, data analysis, optimization suggestions, maintenance, and safety alarms, forming a closed loop of monitoring and feedback integrating "platform discovery, diagnostic analysis, on-site inspection, implementation of rectification, and efficient operation".
High-resolution color touch screen, dynamic operation interface, multi-level operation authority management, and automatic recording of operation parameters, curves, and faults, make the operation more humanized and intelligent.
In fully premixed planar combustion, fuel and oxygen are mixed in a very fine, uniform, planar mixing layer. This mixed layer is ignited, and a flame is formed by the reaction of fuel and oxygen. Since the fuel and oxygen have been thoroughly mixed together, the flame propagates throughout the mixed layer, creating a flat flame pattern. This allows fully premixed planar combustion to be used to study the fundamental properties of flames without being affected by the flame shape.
The convection heating surface of the gas-fired hot water boiler adopts silicon-aluminum alloy heat-conducting tubes, which increases the heat exchange area by 5 times, replaces more heat in the flue gas, and improves heat exchange efficiency. And the use of silicon-aluminum alloy with high thermal conductivity for heat transfer greatly prolongs the service life of the pressure components.
|Types||Thermal power||Steam pressure||Thermal efficiency||Fuel||Power requirement||Length * Width * Height||Weight||Chimney|
|380/50||3370 * 1660 * 1830||2.32||300|
|CWNS1.4-95/70-Y.Q||1.4||3450 * 1820 * 2030||3.04||350|
|CWNS2.1-95/70-Y.Q||2.1||4200 * 1940 * 2420||5.04||350|
|CWNS2.8-95/70-Y.Q||2.8||5230 * 1940 * 2340||5.24||450|
|CWNS4.2-95/70-Y.Q||4.2||6550 * 2340 * 3640||10.08||550|
|CWNS5.6-95/70-Y.Q||5.6||7580 * 2550 * 3780||16.4||700 * 550|
|WNS0.7-1.0/95/70-Y.Q||0.7||3490 * 1710 * 2880||3.33||300|
|WNS1.4-1.0/95/70-Y.Q||1.4||4320 * 1930 * 2200||4.66||350|
|WNS2.8-1.0/95/70-Y.Q||2.8||5340 * 1990 * 3460||8.14||450|
|WNS4.2-1.0/95/70-Y.Q||4.2||6540 * 2330 * 3630||14.21||600 * 450|
|WNS5.6-1.0/95/70-Y.Q||5.6||7260 * 2580 * 3950||19.85||600 * 450|
|WNS7-1.0/95/70-Y.Q||7||7630 * 2730 * 4410||24.72||700 * 450|
|WNS14-1.0/95/70-Y.Q||14||9340 * 3660 * 4690||46.42||950 * 600|